[Beowulf] Opteron cooling specifications?
ballen at gravity.phys.uwm.edu
Mon May 1 23:28:57 PDT 2006
> What breakers are not tested for is the trip time when operated at under its
> current rating. It is not uncommon especially as the breakers age or have
> been tripped repeatedly, to trip at less than 100% of its rating. I've
> replaced breakers many times that would trip when under 80-95% of its rated
> load after several minutes.
I can confirm that I have also seen this behavior. In my experience this
happens after breakers have been run near load limits for months to years.
More information about the Beowulf