[Beowulf] UPS system for Linux cluster
landman at scalableinformatics.com
Thu Apr 30 11:35:05 PDT 2009
Lux, James P wrote:
> Actually, this isn't particularly surprising to folks who deal with
> electrical power. It *is* surprising to folks who see volts*amps (VA)
> and think it means watts.
> Most power conversion equipment has a higher VA rating than Watt
> rating (and, so do most loads, so it works out ok in practice) PF
> (Power Factor) = Watts/VA, and a typical PF is around 0.85.
Most of the advice we've been given about "arbitrary" gear from power
folks has been to use 0.7 (approximately 1/sqrt(2)) as your PF, to
account for varying supply quality and leave an engineering margin (for
error). Indeed, looking at some of the PF curves for supplies under
heavy load shows PF for "85%" supplies dipping into the mid to upper 70s.
Joseph Landman, Ph.D
Founder and CEO
Scalable Informatics LLC,
email: landman at scalableinformatics.com
web : http://www.scalableinformatics.com
phone: +1 734 786 8423 x121
fax : +1 866 888 3112
cell : +1 734 612 4615
More information about the Beowulf